Italy giuliani anello Made Aluminium Pressure Regulator With Built-in Filter FGDR Model
Aluminium pressure regulator with built-in filter, to EN 88-1.
Max. inlet pressure 500 mbar. Max. outlet pressure 350 mbar.
Closure control. Suitable for manufactured gas, natural gas,
liquefied petroleum gas (LPG), non-aggressive gas and air.
Operating temperature range: -15 to 60°C.
Inlet pressure range P1:
FGD: +5mbar up to 200mbar
FGDR: +30mbar up to 500mbar
FG1B: +30mbar up to 1bar
Operating Range P2 : neutral spring standard supply; other ranges
according to the spring table.
Standard Reference :
FGD- FGDR: EN 88-1
FG1B : EN 88-2
Governor Class :
FGD – FGDR :class A
Closing Pressure :
FGD:this model doesn‘t feature test closing
FGDR:in according with Standard EN 88-1
Resistance: according to EN13611 specifications.
Fuel : Gases of three families: manufactured gas (town gas);natural
gas (group H - methane); liquefied petroleum gas(LPG);
Ambient Temperature Range: -15℃ to +60℃
Operation : by tensioning the spring, without auxiliary energy.
Construction Features: compensation of inlet pressure,standard
supply safety diaphragm, internal pipe impulse. Fast-seal gasket.
All models are supplied with inlet and outlet pipe tap fittings.
Outlet Pressure of FGDR Model Pressure Gas Regulator
|Model||FGDR 15-20-25||FGDR 32-40-50/40||FGDR 50|
|Spring Color||Green||5-15 mbar||5-15 mbar||5-15 mbar|
|Neutral||10-30 mbar||10-25 mbar||10-35 mbar|
|Violet||25-80 mbar||20-70 mbar||30-80 mbar|
|Brown||70-160 mbar||65-130 mbar||70-220 mbar|
|Blue||150-280 mbar||/||210-350 mbar|
|White||270-350 mbar||120-250 mbar||/|
Material: Aluminum body ,inner parts in aluminum ,steel, brass and
synthetic materials; diaphragm and gaskets in nitrile-butadiene
Compensation diaphragm, operating diaphragm and safety diaphragm:
an external breather outlet pipe is not necessary as the
incorporated safety diaphragm ensures that, in the event of
breakage of the operating diaphragm,no gas leakage (over 30 dm3/h)
possible inside the room (in compliance with par.3.3.2. EN88
Install the governor with the diaphragm positioned horizontally (on
horizontal pipes). Be careful to follow always the direction of gas
flow indicated by the arrow on the regulator/governor.
Suitable tools must be used for the regulator/governor fitting on
the inlet and outlet hubs. Never effect leverage on the sleeve of
the upper cover when fitting the regulator/governor.
For all models with the filter inside, the regulator/governor is
best fitted at a comfortable height from the ground so as to
faclitate the filter cleaning (fit always a suitable gas filter
upstream the governor/regulator).
Make sure that the pipes are clean and aligned so the
regulator/governor is not under stress.
Do not remove the perforated diaphragm breather cap (3) and do not
obstruct the hole, otherwise the regulator/governor will not work.
Install the governor so avoiding contact with plastered walls.
Make sure that the regulator/governor is suitable to the intended
|FGDR32||009.0223.101||With neutral spring 10-25 mbar||1-1/4"|
|FGDR32||009.0223.102||With green spring 5-15 mbar||1-1/4"|
|FGDR32||009.0223.103||With violet spring 20-70 mbar||1-1/4"|
|FGDR32||009.0223.104||With brown spring 65-130 mbar||1-1/4"|
|FGDR32||009.0223.106||With white spring 120-250 mbar||1-1/4"|
|FGDR32||009.0223.107||With black spring 240-350 mbar||1-1/4"|